Becht Engineering Blog
In this section of the site contributing authors submit interesting articles relating to the various services, industries and research & development efforts of Becht Engineering.
Becht Engineering staff are experts in piping, and include former chairman of various ASME piping committees, including ASME B31.3. Becht Engineering performs detailed design for complex piping systems including very high temperature and pressure systems such as piping for FCC flue gas expanders and high pressure LDPE systems, as well as design, a
nalysis, troubleshooting and fitness for service evaluation of piping.
Pump Trips and Check Valve Closure
Thursday, 16 May 2013
Pump Trips and Check Valve Closure Systems running multiple pumps in parallel can undergo serious equipment and piping damage during a pump trip caused by a power outage or pump mechanical failure. Uncontrolled reverse flow in the system can occur and if improperly selected check valves are used it can result in pumps running backwards or transient pressure spikes in the system, i.e., water hammer. Water hammer will occur if reverse flow occurs prior closure of the check valve and the effect increases with higher reverse flow velocity. Becht has worked with clients on analysis of the design of their systems, e.g., a water treating facility running multiple 52,000 gpm pumps in parallel, a seawater pump station pumping cooling water through a several mile pipeline to an inland facility and a boiler feed water circulation system for a 3000 psig forced circulation boiler. In a three pump system (two operating...