In addition to the many clarifications, updated references to codes and standards, updates to basic allowable stresses, and added listed materials, there are several substantive changes to the 2016 Edition of ASME B31.3, Process Piping, which is scheduled to be issued mid-January 2019. These substantive changes are:
Added specific permission for the owner to designate a representative to carry out selected responsibilities required by this Code, and noted that the owner retains ultimate responsibility for the actions of the representatives.
Added the ASME B&PV Code Section VIII, Division 2, para. 4.16 flange calculation method as an acceptable way to design flanges for B31.3 applications. The Division 2 procedure considers pressure, gasket seating, and externally applied axial forces and net-section bending moments.
Added specific references to ASME B31J-2017 as a resource for stress intensification and flexibility factors as an alternate to Appendix D.
Added Appendix W, which describes an alternate method for evaluating high cycle fatigue when specified by the owner. The method in intended to be used when the number of significant stress cycles exceed 100,000.
A significant stress cycle is defined as a cycle with a computed stress range greater than 20.7 MPa (3.0 ksi) for ferritic and austenitic steels. For other materials. or corrosive environments, all cycles shall be considered significant unless otherwise documented in the engineering design. The existing rules provide an acceptable method of evaluating piping systems for fatigue when the number of significant stress cycles is less than or equal to 100,000. The piping cyclic loadings may be due to thermal expansion, anchor motion, vibration, inertial loads, wave motion or other sources.
Added explicit language requiring heat treatment for structural attachments welded directly to pressure-containing materials when the piping is required to be heat treated.
Added a definition for readily-accessible: those surfaces that can be examined from not more than 600 mm (24 in.) and at an angle not less than 30 degrees to the surface to be examined.
A fatigue analysis is required for all piping systems in Chapter IX High Pressure Fluid Service. In previous editions, this analysis was permitted to be performed in accordance with the BPV Code, Section VIII, Division 2 or Division 3. Division 2’s fatigue analysis involves using a standard S/N curve to determine the design fatigue life. Division 3 also allows an S/N curve approach, but only if it can be shown that the piping component will fail in a leak-before-burst mode. Otherwise, a more rigorous fracture mechanics evaluation is required. The Division 3 S/N analysis contains several requirements that are not included in Division 2, such as surface finish and mean stress corrections. Because the Division 2 approach is less precise than the Division 3 approach, wherever possible, Division 2 was eliminated as an option for the required Chapter IX fatigue analysis.
Have a question or need more information? You may post a comment on this blog for the author below. If you have a question about Becht Services you may click the link below.
Mr. Frikken is an internationally recognized authority in piping systems, valves, and the development of standards and specifications. His work with Becht includes designing new piping systems, analyzing existing piping systems, assisting manufacturers with respect to code compliance issues, and providing instruction on process piping and piping flexibility analysis courses. Don has received a number of awards including the ASME B31 Forever Medal for Excellence in Piping, and the ASME Melvin R. Green Codes and Standards Medal in 2002, which recognizes outstanding contributions to the development of documents used in ASME programs of technical codification, standardization and certification.
He received the ASME Fellow Award in 1994 and the ASME Dedicated Service Award in 1995. Prior to joining Becht Engineering, Don spent 34 years with Solutia, Inc. and Monsanto Company working on a wide range of activities including piping and mechanical design, project engineering, and engineering standards. Mr. Frikken is a registered PE in Missouri.
Click to View Becht’s 2018 Technical Training Public Course Calendar