Becht Engineering Blog
In this section of the site contributing authors submit interesting articles relating to the various services, industries and research & development efforts of Becht Engineering.
Subscribe to this list via RSS
How To Quantify And Evaluate Oil Storage Tank Annular Plate Corrosion
Sunday, 18 November 2018
Nadarajah "Ranjan" Chithranjan
Materials Degradation and Corrosion
Failure of Oil Storage Tank Annular Plate
In the past ten years, there have been a few oil storage tank annular plate failures due to soil side corrosion and fatigue loading (filling and emptying) which has led to large spills. The corrosion tends to be localized in a groove fashion and the size of the flaw could vary from 3 feet to 12 feet in the circumferential direction. The location of the corrosion is also where the highest bending stress will occur during filling and emptying of tanks. See Figures 1 and 2 for the location of the failure on the annular plate. Since the location of failure is under the tank, the corrosion flaws cannot be detected easily from the outside of the tank. It can only be detected if an internal inspection is done which would require the tank to be emptied and cleaned and this is very expensive. However, with UT shear wave...